To embed this BIM object onto your website, simply copy and paste the HTML code below.
<iframe src="https://www.nationalbimlibrary.com/en/syndicationgeneration/iframesingle/?objectId=247332" frameborder="0" width="225" height="285"></iframe>
The object content is configured for use in UK, but it may also be suitable for use in other locations.
Cold Water or LPHW Services - Multi-Circuit, Distributed Digital Control System, Single or Multi-Application: For Multiple trace heating applications. The circuits shall be controlled and monitored using a centralised control system with distributed power and control modules, complete with colour LCD touch screen, password protected user interface terminal (UIT) for central programming; power connection modules (PCM) to provide distributed power, circuit protection, control & monitoring; remote monitoring modules (RMM) for additional temperature measurement; integrated energy saving proportional ambient sensing programmable controller (PASC); BMS interface using ProtoNode high performance multi-protocol gateway, to allow translation from native ModBus to BacNet protocols; pre-programmed parameters, to deliver concurrent control for heating cables used for pipe freeze protection, hot water temperature maintenance, flow maintenance, surface snow melting, roof/gutter de-icing and floor heating applications. 20 Amp or 32 AMP switching capacity per a circuit The PCM also provides: Ground Fault Monitoring, Line Current Monitoring, Alarm Capability and RTD (Resistance Temperature Detector) input capability for each individual module heating circuit.
Your query has been sent.
A technical consultant from will be in touch soon.
Manufacturers using NBS National BIM Library adhere to our code of conduct.
The creation of BIM objects for the inclusion on the National BIM Library includes Omniclass classification codes and titles.
Copyright © 2014 the secretariat for the OmniClass Development Committee. All Rights Reserved. http://www.omniclass.org/