To embed this BIM object onto your website, simply copy and paste the HTML code below.
<iframe src="https://www.nationalbimlibrary.com/en/syndicationgeneration/iframesingle/?objectId=216765" frameborder="0" width="225" height="285"></iframe>
Select regional version:
The object content is configured for use in UK, but it may also be suitable for use in other locations.
Control panel for the CARE2 EVC system. The panel is fitted with 4-way line card (expandable up to 16-way). Up to two control panels can be fitted per system or add Network Expansion Panels (NEP) for further system expansion. Each panel can be connected to up to 16 outstations).
Outstations are radial wired from the control and NEP panels using enhanced 2-core fire rated cable. Control panels and NEP panels on the system are cabled in a loop configuration using 2x2 core enhanced fire rated cable - max length of loop 5km.
The panel features an LCD screen and rotary encoder for control. The rugged red handset (with hearing aid compatible earpiece) is housed behind a lockable door. System configuration is stored on an SD card.
Batteries required for system backup are housed within the panel enclosure. Fully BS5839-9 compliant. Object options include black or stainless steel finish units which can be selected as either surface mounting or flush mounting items.
Your query has been sent.
A technical consultant from will be in touch soon.
Manufacturers using NBS National BIM Library adhere to our code of conduct.
The creation of BIM objects for the inclusion on the National BIM Library includes Omniclass classification codes and titles.
Copyright © 2014 the secretariat for the OmniClass Development Committee. All Rights Reserved. http://www.omniclass.org/