To embed this BIM object onto your website, simply copy and paste the HTML code below.
<iframe src="https://www.nationalbimlibrary.com/en-gb/syndicationgeneration/iframesingle/?objectId=255594" frameborder="0" width="225" height="285"></iframe>
The object content is configured for use in UK, but it may also be suitable for use in other locations.
An extended set version of MK-6/HY™. The sprayed material bonds tightly to the substrate forming a durable surface that does not dust or flake. Being gypsum based however, it is not designed for permanent exposure, or exposure to extreme weather conditions. To achieve accelerated set during application (15 minutes), Monokote® Accelerator must be injected into Monokote® MK-6/HY™ ES™ at the nozzle of the spray gun.
Features and benefits:
||BS 476-21, BS 476-6 and -7|
||An extended set version of MK-6/HY™; the material can be left in the spray system for up to 5 days and is a spray applied structural fire protection system, low density gypsum plaster with enhanced set characteristics and product yield|
||Designed for concealed commercial applications, for use on steel framed structures and concrete soffits, can be applied from one central pumping station to a building of up to 50 storeys|
||Monokote MK-6HY ES|
||GCP Applied Technologies|
||Not begin until the contractor and applicator have determined that the surfaces are acceptable to receive the fireproofing material|
||Seek advice from GCP regarding certain substrates, e.g. primed steel and all concrete surfaces|
||260 kg/m³ (16 pcf)|
||All surfaces to receive spray applied fireproofing shall be provided free of oil, grease, paints/ primers, loose mill scale, dirt or other foreign matter which may impair proper adhesion, other trades shall install clips, hangers, support sleeves and other attachments required to penetrate the fireproofing prior to application, other trades shall not install ducts, piping, equipment or other suspended items until the fireproofing is complete, complete placing of concrete on floor and roof decking prior to the application of the fire-protection to the underside of the deck, beams and joists, protect surfaces in the immediate spray area that are not to be coated with suitable masking, drop cloths or other satisfactory covering|
||Carry out before installation commences|
||An air and substrate temperature of 4.5°C minimum shall be maintained for 24 hours prior to application, during application and for a minimum 24 hours after application, provision shall be made for ventilation to properly dry the fireproofing after application. In enclosed areas lacking natural ventilation, air circulation and ventilation must be provided|
||10 mm - 84 mm|
||Class 0 to BS 476-6 and -7|
Your query has been sent.
A technical consultant from will be in touch soon.
Manufacturers using NBS National BIM Library adhere to our code of conduct.
The creation of BIM objects for the inclusion on the National BIM Library includes Omniclass classification codes and titles.
Copyright © 2014 the secretariat for the OmniClass Development Committee. All Rights Reserved. http://www.omniclass.org/